[ RadSafe ] Tritium production in a nuke plant
rahim.ghanooni at gmail.com
Thu Apr 18 23:41:40 CDT 2013
Thanks for the suggestion, yes we have GALE and used it. This is the
problem with GALE.
GALE is designed for a typical 600 to 800 MWt PWR, or BWR. We are
designing a modular reactor 45 MW, and we do not have many of the systems
that other nukes have (WWW. NUSCALEPOWER.com).
I manually calculated the radionuclide inventory in the reactor coolant and
the steam generator, using nureg-0017, then creating a spreadsheet
determining the gaseous and liquid effluent. NRC requires to calculate
C-14, Ar-41, and T. The first two are calculated, and I am trying to get
more information on T. I also calculated the fuel depletion, and by the
time I finish determining the T activity, I am done with the source term,
then start shielding calculation and dose assessment.
On Thu, Apr 18, 2013 at 8:29 AM, <JOHN.RICH at sargentlundy.com> wrote:
> You probably haven't used the "GALE" codes (NUREG-0016 and NUREG-0017) for
> a long time. They address tritium production and release. They're a
> little old but they were NRC approved. It might be worth considering
> using these codes again if nothing more current meets your needs.
> - -jmr
> John Rich
> You are currently subscribed to the RadSafe mailing list
> Before posting a message to RadSafe be sure to have read and understood
> the RadSafe rules. These can be found at:
> For information on how to subscribe or unsubscribe and other settings
> visit: http://health.phys.iit.edu
More information about the RadSafe